In order to ensure safety, reliability and meet the heating demand, through scientific management, improve the operation level, so that the boiler can achieve high efficiency and low energy consumption. Shandong Gas Boiler Factory specially formulates this operation regulation, hoping to be helpful to everyone.
1. Adjustment of working conditions: In the operation of gas-fired boilers, duty personnel should adjust the combustion conditions to keep the pressure, temperature, circulating pump and water supply pump of the boilers in stable working conditions. Regular sewage discharge, at least once per shift, and under low load conditions;
2. Load regulation: Heating load regulation is the key link in the economic operation of boilers. Gas-fired boilers should not run under 70% of the rated load regularly or for a long time (not single low water temperature or multiple small fires). Load regulation method:
(1) Formulating temperature control curve: The heat supply and outlet temperature curve of the boiler should be calculated comprehensively according to heating area, heat consumption index, building envelope structure and regional climate. The temperature curve of the boiler operation can be used as the basis for the adjustment of the boiler operation load, and the load can be adjusted by the attendants according to the changes of outdoor temperature and indoor temperature.
(2) Scientific and rational regulation: Load regulation includes two methods: operation number regulation and boiler temperature regulation. First is the quality control (temperature control), second is the quantity control (pump regulation):
Boiler effluent temperature regulation: Temperature regulation is based on outdoor temperature change, but should not be adjusted frequently. It is reasonable to regulate 2-4 times a day. For more than three boilers running in parallel, the outlet water temperature should not be set at more than 65. The outlet water temperature setting should be adjusted according to the outdoor temperature.
Boiler operation number adjustment: The number of operation stations is adjusted by the on-duty personnel according to the temperature difference between the total supply and return water. The temperature difference between supply and return water reflects the relationship between boiler heat supply and heat consumption, and is an important index to measure boiler thermal efficiency. Small temperature difference, large heat supply, large temperature difference, small heat supply. The reasonable range of temperature difference should be between 8 and 12 degrees Celsius. Adjustment measures:
Reduce the number of circulating pumps: In the initial stage of heating, low load operation can be adopted to reduce the number of circulating pumps. For the multi-parallel circulating pump temperature difference frequency conversion system, the temperature difference should be maintained between 5 and 8 degrees Celsius. It can be achieved by setting the temperature difference of the frequency converter.
Increase the number of circulating pumps: In the medium term of heating, according to the range of indoor temperature and outdoor temperature, the number of circulating pumps should be increased according to the temperature difference between 8 and 12 degrees Celsius. For the multi-parallel circulating pump temperature difference frequency conversion system, the temperature difference has been set to automatically adjust, but the number of operating stations is controlled by the on-duty personnel.
Well, today's wonderful content will be introduced to you here, I do not know you have any questions about Shandong gas boiler? Welcome to our official website: online customer service staff at http://www.mjingoma.com!